Block diagram of the active harmonic filter is considered. State table inverter power switches active harmonic filter is considered. Calculated the capacitance on the DC link active harmonic filters. The calculation takes into account the power converter losses in the active harmonic filter.
Keywords: active harmonic filter, distortion power, energy storage capacitor
A long term study of compensation converters allowed to solve the task of designing the structure, the calculation of its elements, the determination of static characteristics and energy performance. Thus remain undeveloped algorithms of their work to ensure a successful use of compensatory converters and independent control of active and reactive power consumption. An algorithm of their work to ensure the optimal use of compensatory converters. This article contains material from GC № 16.526.12.6016 11.10.2011.
Keywords: Site load electric network compensation converters; management algorithms ; controlled electric drive with compensation rectifier in section of the direct current of the converter of the frequency
An optimal control algorithm for compensating converters. This algorithm provides control of active and reactive components of power consumption. The algorithm allows to reach a balance between the values of the angles controls αi and αe . In the algorithm used is a method for solving equations by iteration. In article materials of the state contract № 16.526.12.6016 on 11.10.2011.
Keywords: compensation converter, frequency converter, control algorithm, objective function, iterative method